Universal Biotube® Pump Vaults can house one or two Orenco® high-head
effluent pumps. They are used to filter out up to two-thirds
of the suspended solids from wastewater effluent flowing from
septic tanks or separate dosing tanks in onsite wastewater systems
and effluent sewers.1 Effluent enters through inlet holes around the
perimeter of the vault and flows through the Biotube effluent filter
cartridge to the external flow inducers. The filter cartridge can be
removed without pulling the pump or the vault.
Vaults are suspended in a tank by two Schedule 80 support pipes.
“Earless” vaults that rest on the bottom of a tank are also available.
The tank depth and float settings must be known in order to select the appropriate PVU for the system. Once float settings are determined, select a pump vault that will satisfy the required float settings and also position the pump vault inlet holes at their optimum elevation.
Step 1: Determine tank depth (TD). Tank depth is measured from the inside bottom of the tank to the outside top of the tank.
Step 2: Determine cartridge height (CH).
Step 3: Determine float setting elevations for the system. Float settings are measured down from the outside top of the tank (bottom of pump vault support pipes) to the center of the float collar.
Step 4: Select the proper vault height (VH) by selecting the proper tank depth range on the chart below with the matching cartridge height (CH). Verify that the off point (OP) you calculated in Step 3 falls within the range listed in the “off point range” column.
Step 5: Verify that the off point (OP) is above the minimum liquid level of the pump (MLLp) using the following equation: TD-OP > MLLp + G.
Ronald Crites and George Tchobanoglous. Small and Decentralized Wastewater Management Systems. Boston: McGraw-Hill, 1998.